When the device configuration is done, you can download it to the device so that you can achieve the desired functionality. To do so, you can simply tap the 'Download' button (1) from the main toolbar.
The 'Download' button is only enabled (i.e. not grayed out), when the configuration of the devices to be downloaded has been modified since the last download.
This action will immediately start the download of the configuration from all the devices in the active room as well as in the elements below in the topology (i.e. Cabinet).
At this stage, and if it is the first time that you download the configuration to your devices, you have to locate and press the programming button of the device to be downloaded, since ETS Inside will perform a full download. If you have already downloaded your device configuration, the you do not need to press the programming button, since ETS Inside will perform a partial download and will download only what has been modified.
Additionally, if you try to download an Individual Address to a device and that Individual Address is already assigned to another device of the installation, ETS Inside will automatically unload the conflicting device so that you can proceed with the download as requested.
In our example, the programming button of the actuator looks like that:
This differs of course from manufacturer to manufacturer. When the programming button is pressed, the download starts and you can see the progress of the download on the left column (1).
When the download operation of a device is completed, it disappears from the list of pending operations.
As soon as all the downloads are completed, you will be redirected to the page where you have initiated the download. The installation is ready to work!