remote connection ets to project
I have to make a change in a project that is far away.
Can I connect to the project via the internet so that I can work on it with my ets5?
If so, what is the best solution?
Assuming the local project has an KNX IP gateway for reaching the KNX/EIB network, then I suggest you set up a VPN connection that connects to the local network where the KNX IP gateway is reachable in. Once you connect to this VPN, ETS should be able to discover the KNX IP gateway and you should be able to connect to it. Alternatively. I'd suggest you run ETS on a local machine over there, and take over the screen using TeamViewer, LogMeIn, VNC (over VPN) or alike.1
I use VPN to try to connect to a remote location, ping to the IP router works, but I get no connection in ETS - what can be wrong? The connection does not show up. Is it something wrong with local IP on my computer?-1
Please sign in to leave a comment.